J. SOLOTKEN AUDIT & RETROFIT
Owner: J. Solotken
J. Solotken & Company, Inc. purchased an existing 123, 500 sq. ft. warehouse/office building which needed a complete power & lighting update. After perfoming and energy audit, ERMCO completed work on this renovated space which resulted in lowering the buildings’ lighting energy use from 110 kW to 33 kW, while maintaining the same or improved foot candles and CRI. The work also involved complete building lighting controls and occupancy sensors.
Also, in a joint effort with IPL to improve poor power factor (an estimated .50), ERMCO changed the service entrance to this facility by replacing an outdated over-head 1000A/480V Delta ungrounded service with a pad-mounted, underground 800 A/277~480 Wye service.